800W AC220V Outdoor Cabinet Air Conditioner,For Outdoor Telecom Shelter/Room/Base Station
The AC Air Conditioner is a full automation temperature control product. It uses intelligent controller to control the whole system of the air conditioner. According to the variation of environment temperature, the intelligent controller can automatically detect, operate and record the whole system’s operating time, power consumption, event and historical data. It can store 100 event records and 1280 historical data records, and can enquire 256 days’ daily record information. The product is widely applied in telecom cabinet, small and medium sized telecom room, UPS room, outdoor base station room, etc.
(6)Low energy consumption
(7)With 4 way switching value detection
(8)With 1 way room air conditioner control
(9) Voltage input range: 220VAC±25% 50/60Hz
(10) With dry contact alarm output
3.System Principle Diagram
Diagram 1: System Principle Diagram
||Safety of household appliance and electrical appliance with similar use.
||Environmental conditions existing in the application for electric and electronic products - storage
||Environmental conditions existing in the application for electric and electronic products - transportation
||Environmental conditions existing in the application for electric and electronic products - usage
|working environmental temperature
||-20°C ~ 55°C
|storage working temperature
||-50°C ~ 70°C
||rated cooling capacity
|heating input power
|rated input current
|rated input power
(187V ~ 264V)
Diagram 2: Dimension Diagram
6. Installation and Electrical Wiring
6.1 Preparation Before Installation
(1) Prepare the tools in the following table “Installation And Maintenance Tools”.
(2)Check the air vents to ensure there’s no unnecessary items on the vents.
6.2 Installation And Maintenance Tools
||Fix air conditioner.
|Small Slotted Screwdriver
||Wire power supply port on the panel
||Crimp power supply for equipment
||Check the wiring to ensure it’s correctly connected and without short circuit.
||Test operating current of the air conditioner
6.3 Installation Steps
(1)Make sure the air conditioner is not connected with power.
(2)Fix the air conditioner according to the Dimension Diagram.
(3)Strip the insulation of the power supply wire, and crimp the terminal.
(4)Connect the wires according to the Electrical Wring Diagram.
(5)After finishing the wiring, use the multimeter to check if the electric circuit is normal. Then connect the air conditioner with power supply, and use clamp meter to test the operating current.
Note: Make sure to disconnect all the power supply to the air conditioner before installation. Choose proper wire diameter and test operating current according to the technical parameters of the air conditioner.
6. 4 Electrical Wiring Diagram
Diagram 3 Electrical Wiring Diagram
L N PE : power supply port (voltage input: 220VAC±25% 50/60Hz)
A+ B- GND : communication port
AL1 AL2: general alarm output port
F+ F- : direct ventilation output port
N : not connected pin
7. After mechanical installation and electrical installation are finished, check the installation items.
(1)Make sure the air conditioner is firmly installed.
(2)Check the electrical installation circuit, and ensure it doesn’t have short circuit.
(3)Check the air outlet, air inlet, internal fan and external fan of the air conditioner, and ensure they don’t have any odds and ends.
(4)Connect the air conditioner to power supply, and test the power supply (voltage input: 220VAC±25% 50/60Hz), operating current 1A±4%.
8. System Control
8.1 Control Board
a.2×16 Chinese/English shift LCD display, user friendly;
b.Simultaneously display temperature and humidity inside the box and communication room temperature;
c.Temperature measurement accuracy: 0.1 °C; humidity measurement accuracy:5%;
d.Can store 180 days’ daily event record, 1 record every day;
e.Daily highest temperature, lowest temperature, average temperature
f.Daily event record;
g.Save the former day’s daily data at 0:00 every day; Can query 180 days’ daily record information;
h.RS485 communication,RTU-Modbus protocol, support remote detection and control;
i.Controllable air conditioner quantity:2 sets. 1 set of air conditioner for communication room, and 1 set of small air conditioner for thermostatic box.
j.Control mode: pulse (Non dry contact air conditioner), conducting (dry contact air conditioner)
k.Real-time control air conditioner on/off
l.Power supply: AC85V~265V/50HZ；
n.Working environment: -30°C~70°C；<90%RH；
o.Installation method: guide rail,hanging;
It uses English interfaces, which can be operated easily. All the operations can be realized with four buttons. The following is the control board diagram:
Diagram 4 Control Board Diagram
PgDn:page down button, confirm button.
Press once and release the button, page down;
A long press on the button, enter or exit parameter status;
At operating status: can select three display interfaces;
At parameter status: revise, confirm and parameter page down button; a long press on the button to exit parameter status.
▲:increasing parameter revision. Page down button for event query.
▼:decreasing parameter revision. Page up button for event query.
PgUp: page up button; the function is oppose to PgDn operation.
8.3 Operating Interfaces
The controller includes four types of working modes: operating mode, parameter mode, manual operating mode, and query mode.
(1) Operating Mode:
The mode is normal working mode. There are three operating interfaces which can be selected. The three interfaces display different content. When they are not selected, the interfaces will automatically shift. Press the button “PgDn” to select next display interface; press the button “PgUp” to select the previous display interface.
Line 1: temperature and humidity inside the thermostatic box (or area I);
Line 2: box air conditioner status, real time clock;
※ ------- cooling start sign;
☼ ------- heating start sign;
♂ ------- hydrogen exhaust,/direct ventilation sign;
-- ------- compressor/ heater stop working.
Line 1: temperature and humidity inside the communication room (or area II);
Line 2: cabinet air conditioner status, real time date;
※------- cabinet air conditioner start sign;
-- ------- cabinet air conditioner off sign.
Circularly display current alarms;
When multiple alarms occur, it will display each alarm information circularly.
At operating status, long press on the button”PgDn” for around 3 seconds, or press the button”PgUp” at interface 1, to enter parameter mode.The first entered interface is the main menu interface, see the following diagram.
Press the button “▲”, “▼” to choose corresponding parameter group; Press ”PgDn” to enter corresponding parameter group; Press ”PgUp” to return to operating mode. The parameters selection includes:
(a) Observation Parameter (Apar Watch)
(b) Control Parameter Revision (Cpar Update)
(c) Basic Parameter Revision (Bpar Update)
(d) Manual Operation (A/M Select)
(e) Event Query (Event Query)
(f) Return To Operating Mode (Return)
(a)Observation Parameter Group (Apar):
Enter the interface to check some parameters which can’t be checked at operating mode, see “9 Parameters”.
At parameter mode: on the left of line 1 is Parameter No. (PAnn); on the right of line 1 is parameter value. Line 2 shows the remark of the parameter.
(b) Control Parameter Group (CPar):
Enter the interface to observe or revise the parameters which can be revised, see “9 Parameter”.
At parameter mode: on the left of line 1 is Parameter No. (PCnn), on the right of line 1 is parameter value. Line 2 shows the remark of the parameter.
(c) Basic Parameter Group (BPar):
Enter the interface to observe or revise the parameters which can be revised, see “9 Parameter”.
At parameter mode: on the left of line 1 is Parameter No. (PBnn), on the right of line 1 is parameter value. Line 2 shows the remark of the parameter.
(d) Manual Operation:
Enter the interface to select “Cool”, “Heater”, “Air”, “Initpar”, “Aoauto” to conduct manual start and stop operation.
(e) Event Query (Query):
Enter query mode
|Place of Origin: Shenzhen, China (Mainland)
||Rated Cooling Capacity : 800W
|Brand Name: CYNRIN
||Rated Heating Capacity:500W(optional)
||Dimension: H×W×D 352*175*583mm
|Product Name: Outdoor Cabinet Air Conditioner
||Input Voltage: AC220V/50Hz
|Certification: ISO9001, CE, 3C,
||Rated Input Current: 2.2A
|Cover Material: galvanized steel
||Rated Input Power: 484W
||Working Temperature: -20°C ~ +55°C
|Protection Level: IP55
|Installation Mode: door mounted
||Cooling Method: compressor, active cooling
Dimension Diagram: H×W×D: 352*175*583mm
- Remote measuring, remote communication, remote control, which can realize multiple automatic protection and comprehensive self-testing function.
- Strict process control and famous brand components to ensure high quality and reliability of this product
- Fit for harsh condition (T3),R134 a refrigerant
- Multiple self-protection design, RS485 communication port (MODBUS-RTU protocol)
- LED display, all the setting can charge at the field.
- The heating function is optional
- Dry contact alarm output, NO/NC optional
- Anti-theft design, without the protection cover.
The products are widely used in
- electric power
- industrial automation
- rail transit
- CNC machine tools and other fields.
- Indoor and Outdoor Battery Cabinet
- Wireless Indoor and Outdoor Cabinet
- Indoor and Outdoor Hybrid Base station
Payment & Shipping Terms:
|Minimum Order Quantity:
||T/T, L/C, etc
||1,0000 sets per month
||10-15 working days
||carton + wooden case + pallet
1. Q: How about the air cooler material?
A: It makes by 100% new plastic, pure copper for motor.
2. Q: What voltages you can do, could you make special voltages?
A: we can make DC48 and all AC voltage products for you.
3. Q: I want to use our own brand, is it OK?
A: It is possible, we supply the OEM products too.
4. Q: How about the warranty?
A: All the unit warranty is one year.